FREQUENCY OF ELECTRICAL INSPECTIONS/TESTS
Professional Electrical Inspection Tests for Stockport homes and businesses.
Houses in Multiple Occupation
If the property is a house in multiple occupation then the Management Regulations require the manager to take safety measures and to maintain electrical installations.
Very importantly for all HMOs (not just licensable HMOs) there is an obligation to have fixed electrical installations in every HMO inspected and tested at intervals not exceeding 5 years by a qualified electrician. A certificate must be obtained. The local authority can require a certificate to be produced in 7 days if they ask.
The Landlord should carry out a regular basic visual safety check of the electrical installation to ensure that these are safe. This should detect broken items such as sockets and light switches or signs of scorching around the sockets due to overloading or damaged cables etc.
The Institute of Electrical Engineers recommends 10 years as the maximum period between tests of the electrical installation by an electrician but this relates to the period between the initial inspection (when the installation was first installed) and the first periodic inspection/test. Subsequent periods for inspection/tests would depend on the condition of the installation. What the Electrical Safety Council now recommends in this latest Guidance for rented accommodation is that period inspections/tests by a qualified electrician are carried out at least every 5 years or on a change of tenancy. As pointed out above, if the property is a house in multiple occupation of any kind (which will include shared houses) there is a statutory requirement to carry out such inspection/test every 5 years anyway.
The Institute of Electrical Engineers also recommends for residential accommodation that an inspection/test is carried out on a change of occupancy. These are inspections/tests by a qualified electrician.
The Electrical Safety Council Guide says that where a change of tenancy occurs within a short period (for example not more than 6 months) a full inspection/test may not always be required. However, it is imperative that a landlord’s representative carries out a visual electrical safety inspection prior to reletting. This should undertake a manual test of any residual current devices.
As an alternative to a full test/inspection the Guide suggests a visual condition report, also carried out by a qualified electrician. However a visual condition report is only suitable where the installations have been inspected and tested in the last two years and the result was satisfactory or any resulting defects have been rectified.
The Guidance recommends that when providing portable appliances for tenants, the landlord should check that every appliance has a CE mark. It also recommends that you should only provide appliances with additional safety marks e.g. the British Standard Guidance mark or the BEAB approved mark.
Tenants should be provided with instruction manuals and be told to read and follow them.
If you do not undertake PAT tests, the Guidance recommends that portable electrical appliances should be checked by the landlord before letting the property to ensure that there are no cuts/abrasions to the cable, the plug is satisfactory, there are no loose parts or screws, that there are no signs of burning and there is no damage. You are recommended to regularly check them after that.
There is detailed guidance regarding the frequency of carrying out PAT testing. PAT testing must only be carried out by a qualified person. Examples of the recommended periods are as follows:
Portable Equipment – table lamps, fans, kettles, toasters, vacuum cleaners (2Yrs)
There is also guidance by the Electrical Safety Council as to when fire alarms should be inspected/tested. Fire alarm systems need to be regularly tested. The routine tests which are to be carried out frequently do not require specialist knowledge and can either be carried out by the landlord or the tenant. It is essential that a log book record is kept. If the tenant is to be responsible for testing, the landlord must instruct the tenant as to what must be done and periodically check the situation to see if everything is being done (e.g. by checking the log book).
In the case of houses in multiple occupation (i.e. all HMOs; not just licensable HMOs) the landlord is obligated under the management regulations to ensure that fire alarms are in proper working order. The testing/maintenance requirements vary according to the type of system
Routine testing – at least one detector or call point in each zone should be tested weekly. Routine inspections/maintenance – A six monthly service should be carried out by a specialist alarm engineer. This is a full test. Note:in the past the suggested frequency for such tests was 12 months but the latest guidance is now that these tests should be carried out every 6 months in the case of Grade A systems.
Grade B system (interlinked systems where there is no control panel).
These systems should be tested at least once a week by operating all the fire alarm devices. For smoke alarms and heat detectors this can be carried out by use of a test button on each of the alarms.
Routine maintenance – these require periodic cleaning in accordance with the manufacturer’s instructions. Routine inspections – a routine check must be carried out by a qualified electrician every 12 months.